Subject: Fw: Utropolis BK-Pressurised Shaft&Wet Riser
From: "Janice" <[email-masked]>
To: "Rachel Lim" <[email-masked]>, "Jit Ping Wong" <[email-masked]>
Cc: "CK Tan" <[email-masked]>
Date: Fri, 22 Jul 2016 19:06:51 +0800

Dear Rachael/ Ping, 
BOMBA plans has been commented today (22/07/2016) and returned to us for amendment. Information required to be indicated into BOMBA plans as follows
  1.. An additional wet riser at staircase 5 there due to our fire fighting lobby exceeding 45.75m by law 229. 
  2.. Staircase and lift pressurized shaft shall be indicated clearly. 
  3.. Indicated the wet riser tanks and pump, hose reel tanks, sprinklers tanks and pump at sections and elevations manually. However, the writing are required mr. Yew stamp (round stamp or BHYew rectangular stamp) will do. 
  4.. Please be informed that I have worked out the item 1&2 in CAD as attached and verified with Chuah/ Oon M&E engineer. Please note, the affected areas as duly highlighted in pink in the drawings no.101 and 102 will be couriered back for your review. 
  5.. 3 sets drawings are required.
The  courier service is arranged on Monday before lunch. Please revert back by Wednesday/ Thursday in order for me to re-submit drawings to BOMBA for review and endorsement if nothing outstanding. 
Trust the above is in order.
regards
Janice

From: Chuah Beng Aik 
Sent: Friday, July 22, 2016 4:58 PM
To: 'Janice' 
Cc: [email-masked] 
Subject: RE: Utropolis BK-Pressurised Shaft&Wet Riser

Dear Janice,

Please find the revised shaft size for your reference.

Kindly revert if you have any further queries.

Thanks you.

Regards, 

Chuah Beng Aik

Electrical Engineer

PERUNDING P.L.A.

Consulting Mechanical & Electrical Engineers

8-01, Wisma Pantai, Jalan Wisma Pantai,

12200 Butterworth, Penang.

Tel No. : (604) 3337990

Fax No. : (604) 3317337

 

From: Janice [mailto:[email-masked]] 
Sent: Friday, 22 July, 2016 4:27 PM
To: Beng Aik Chuah
Subject: Utropolis BK-Pressurised Shaft&Wet Riser

Dear Chuah, 

Please advise the pressurised shafts and wet risers sizes as attached. The affected areas as duly clouded in the drawings.

Regards

Janice