Subject: Re: PARAMOUNT PLOT 1 - Kitchen Exhaust
From: "Janice" <[email-masked]>
To: "oon yk" <[email-masked]>
Cc: "'Rachael'" <[email-masked]>, "'Jit Ping'" <[email-masked]>, "'Chuah Beng Aik'" <[email-masked]>, "'Perunding Kelana Pg'" <[email-masked]>, "'C&S - Ir. Lai CF'" <[email-masked]>, "'Ooi Ee Sze'" <[email-masked]>, "Edwin Chin" <[email-masked]>
Date: Wed, 27 Jul 2016 17:09:54 +0800

Dear Mr. YK Oon, 
After reviewing the proposed location of the kitchen exhaust, our comments as the following:
  1.. Level 1 - Prefer the ducting shaft hiding behind columns so that not block the frontage of the retails shops and shall be located within the planter box area (common area) not encroaching to the alfresco area (accessory parcel). 
  2.. Level 2 & 3 – suggests to divert the ducting next to the staircase 5 and 6 as duly clouded, to minimize the affect to the frontage 
  3.. Level 4 – proposed fan rooms located at grid line 17 to 20 to be combined and another fan room at grid 32&33 to grid 28&29. The remaining proposed fan room at grid 24&25 whether remain or combine with the fan room at grid 28&29.

Do advise the workability and practicality to the aforementioned in order for us to finalise the car parks and retail shops areas for surveyor to proceed with SIFUS submission sooner. 

Dear Ms. ES Ooi, 
Please be informed that the suggestion to the item 2 will take out some areas from retail shops units 16&21. 

Your attention to the above is required and appreciated.

Regards
Janice
BH YEW ARCHITECT

15th Floor, AmMetLife Tower,

No. 1, Jalan Lumut, 50400 Kuala Lumpur

T +603 4043 1346 (ext. 300) l F +603 4043 1349

E [email-masked]  

From: oon yk 
Sent: Sunday, July 24, 2016 2:08 PM
To: 'Janice' 
Cc: 'Rachael' ; 'Jit Ping' ; 'Chuah Beng Aik' ; 'Perunding Kelana Pg' ; 'C&S - Ir. Lai CF' ; 'Ooi Ee Sze' 
Subject: RE: PARAMOUNT PLOT 1 - Kitchen Exhaust

Dear Janice,

Please find the attached Kitchen exhaust riser plotted in for review. Ground floor now will be utilised as F&B outlet with the shop facing front provided with kitchen exhaust ductworks. for Level 2 & 3, the shop number 17 to 20 will also provision as F&B. 

Please note the exhaust ductwork plotted is dimension of duct and box up using brick works shall be provision. please advice the location of the riser if need to be shifted. Thanks. 

All F&B shop as discussed with Ms. Ooi, i suggest to provision for fixed louvers for fresh air intake for kitchen exhaust make up air. The dimension (3500mm x 450mm) taken to be the largest air volume which is 5100CFM in order to standardized the size of louvers for all F&B. 

Thanks.

Regards,

Oon