Subject: Utropolis BK-Commented Toilets Detailed Dwgs
From: "Janice" <[email-masked]>
To: "Jit Ping Wong" <[email-masked]>
Date: Tue, 23 Aug 2016 16:11:41 +0800

Dear Ping, 
Append herewith the comments for COMMON toilets detailed drawings for your action to be taken.
  a.. certain toilet layout miss-out grid line. 
  b.. wall tiles setting to be indicated, from the drop start full piece and what ever left over will be covered with ceiling. 
  c.. Please specify (MV) mechanical ventilation in the plans 
  d.. floor trap to be relocated underneath counter top, and position as sketched (do not put in the middle of tiles) as attached. 
  e.. dimension should not be overlapping 
  f.. a rc curb in front of serviced duct riser 
  g.. lactation room not required mirror 
  h.. dotted circle showing the turning radius within the OKU toilets 
  i.. specify the material for the near by areas such as corridor/ walkway/ etc.. 
  j.. specifications to be revised as attached 
  k.. specify the toilets door type 
  l.. specify toilet paper holder 
  m.. OKU toilets and lactation rooms need to box up for 80mm diameter vent pipe, 150mm soil pipe and 150mm ventilation ducting from level 2 start. 
Please tact me if do not understand.
Regards
Janice