Subject: Re: Discrepancy
From: "Janice" <[email-masked]>
To: "Jit Ping" <[email-masked]>
Cc: "CKTan" <[email-masked]>
Date: Mon, 10 Oct 2016 19:30:42 +0800

Dear Ping, 

Good job. 

Yes, Changes to GA will be updated after tender drawings. another item to add in the GA is 2 nos of the grid lines (42a and 42b to be added).

Append herewith the commented tender drawings for your action:

1.          RCP Details

             a.          Retails shops from level 1 to level 3 WITHOUT ceiling, skim coat finish to be applied

             b.          Additional ceiling details are required as samples attached. 

2.          Podium Car Park Details

             a.          Please revise car park slab fall from 1: 200 to 1: 110

             b.          Re-name the column guard detail to Podium Car Park detail and adds legend as sketched – chamfered column affected area.

              c.          To add scupper drain details, key plan, and fall direction. scupper drain blow up refer to the typical which we have done.

3.          Fire control room&all tanks room

As mentioned to you previously and sketched on 21/09/2016, the door size shall follow the MS 1064 part 1 as attached. Standardise the door sizes to 1800mm and 1500mm for all the tanks room and shall swing out for the services room. 

4.          Surau

Please revise surau as per sketched (rectangular shape bigger space and easy for construction as well). The original layout is not work, the space between ablution and entrance foyer is too narrow not practical for both male and female rooms.

I realised certain tender drawings commented on 23/09/2016 and 27/09/2016 yet to be revised. Please revise it accordingly, do not leave out. 

Thanks and regards

Janice

From: Jit Ping 
Sent: Monday, October 10, 2016 6:40 PM
To: Janice 
Cc: CKTan 
Subject: Re: Discrepancy

Dear Janice,

For the landscape drawing, they will revise and resend again. Then only the team will update accordingly.

The changes for OKU ramp and 2400mm retails’ frontage as mention in previous email,
- OKU ramp will update in spa drawing, the 2400mm retails' frontage only will update after tender as in our previous conversation. 

GA drawing,
The GA drawing will be revise again after the tender drawing. Currently the team is concentrate on tender. The following Items to revise:
1. 2400mm frontage
2. Refuse (latest drawing from stream date 28/09/2016)
3. Landscape level 9.

Please check the dropbox for the detail update today:
1. Surau
2. Louver (have modify according to your reference)

Thank you.
Regards,
Ping

From: Janice 
Sent: Monday, October 10, 2016 4:49 PM
To: Jit Ping 
Cc: CKTan 
Subject: Re: Discrepancy

Dear Ping, 
Good job, keep it up.

Our GA, SPA and tender drawings shall be updated as per landscape latest drawings 15052-PD-00- Master Plan.
Please proceed accordingly.

Regards
Janice 

From: Jit Ping 
Sent: Monday, October 10, 2016 2:14 PM
To: Janice 
Cc: CKTan 
Subject: Discrepancy

Dear Janice,

1.) Discrepancy found at the L9 landscape drawing, Drawing (15052-PD-00- Master Plan) from you on the date 04/10/2016 different with the details drawing (jogging path) from Landart landscape architect at the Drop box which sent at the same day. One of the design in curve, another in the square. Will call and verify with Landart.

2.) Landscape drawing, the staircase ST8 should at grid 36. The basket ball field need to be slightly shift to the right. below are the reference - (For your information). will call and verify with Landart 

Figure 1 (Landscape drawing)                                                    Figure 2 (architecture drawing)

Thank you.
Reards,
Ping